Any Emergency Evacuation lighting system shall be inspected and maintained in accordance to procedures specified in AS / NZS 2293:2:1995. Inspection and testing procedures shall be carried out at intervals of not greater than six months.
A check should be made to ensure that no interruption to the normal supply has taken place for a period of at least 16 hours prior to conducting a discharge test.
Complete and / or verify accuracy of new or existing asset register / log book and enter all relevant and required details.
Check and complete visual inspection of all existing equipment to ascertain that charge circuits, indicators and fluorescent tubes and bulbs are functioning correctly and free from defects to ensure accurate test results.
Operate the luminaries from their battery supply by simulating a power failure from local electrical distribution board. All luminaries shall remain illuminated for not less than the required in service duration (90 minutes minimum for existing systems). All repairs will be repaired if you require.
Restore system to normal mains operation cycle upon completely discharging the system and enter test results in. Insure all existing Luminaries are on standby mode.
Clean light emitting surfaces and light diffusers as required.
If need more other information,you can inquiry from China emergency exit lighting manufacturers Sunwindled.